3200A three-phase, neutral and earth Load Bank Connection designed to restore power to critical applications. The 3200A Generator Connection Point can be fitted inside or outside of a building, allowing a safe and quick connection of load bank to your generator when required.
- Incomer: 3P + N + E 500A Powerlock Drain . Protection: N/A
- Outgoing: 10 x 10 copper bars c/w M12 clearance holes. Protection: N/A
- Dimensions: H18350 x W950 x D360 (mm)
- Weight – 150kg
Equipment housed within a steel enclosure. Powerlock (Drain) connections to 100x10mm copper bars with 300mm spreading distance for bottom entry outgoing cables. 3mm aluminium top and bottom gland plates are provided for the customer
Dark Grey (RAL7021) textured powder coated stainless steel construction (1.4003 grade). Other colour options maybe available by request. Powerlocks mounted on a 45 degree angle aluminum plate. 3mm aluminum top and bottom gland plates are provided. Assembled to IP54.
We recommend the generator should be connected / disconnected when off load and not running. No voltage should be present at the powerlocks. We would also recommend following the convention of connecting in the following order: Earth – Neutral – L1 – L2 – L3. Then disconnecting in the reverse order.
All temporary power distribution equipment is manufactured by IDE in the UK and tested to BS 7671 (12 Months Certification). The products used within our distribution systems conform to EN 60309, EN 60529, EN 60947 and have a 12 month warranty.